Model Number: VV,VY,Z-VV,N-VV,VLV,LVY
Type: Insulated, Low Voltage
Conductor Material: Copper
Conductor Type: Solid
Insulation Material: PVC
Packaging & Delivery
Packaging Details:Wooden, Steel-Wooden Drums or according to customers' request
Delivery Time:according to cusotmers' request, usually 2~4 weeks
-Standard: GB, IEC,JB
-Reliable high quality, competitive price
-Various kinds on optition
It is manufactured according to GB/T12706-2008 standards.
The flame-retardant character complies with GB/T19666-2008.
It is used for transmitting and distributing power on the A.C power line with rated voltage 0.6/1kV.The flame-retardant power cable is suitable for the environment with flame-retardant demand. Fire-resistant cable is suitable for densely populated area, such as high-rise building,the big market, etc.
*The max continuous normal operating temperature of the conductor is no more than 70°C, and the temperature of the conductor will not exceed 160°C at short circuit (no more than 5 seconds).
*Installing environment temperature should be above 0°C and should be preheated if not when being. The minimum bending radius of cable should be no less than 15 times of the external diameter of cable.
*Frequency withstand voltage test: 5Uo+2kV/5min will not breakdown
The bundled firing test of flame-retardant cable and low smoke low halogen flame-retardant cable complies with GB/T18380.3 standards.
4. Type,Designation & Applicable Occasion of the cable
|Type||Product name||Applicable Occasion|
|VV||VLV||PVC insulated PVC sheathed power cable||Lay indoors, in tunnel, underground and in canal. Unable to bear external mechanical pulling force and pressure.|
|VY||VLY||PVC insulated PE sheathed power cable|
|Z-VV||Z-VLV||PVC insulated PVC sheathed flame-retardant power cable|
|DDZ-VV||DZ-VLV||PVC insulated PVC sheathed low-smoke low-halogen flame-retardant power cable|
|N-VV||--||PVC insulated PVC sheathed fire-resistant power cable|
|VV22||VLV22||PVC insulated PVC sheathed steel tape armored power cable||Lay underground, able to bear minor external mechanical force|
|Z-VV22||Z-VLV22||PVC insulated PVC sheathed steel tape armored flame-retardant power cable|
|DDZ-VV22||DDZ-VLV22||PVC insulated PVC sheathed steel tape armored low-smoke low-halogen flame-retardant power cable|
|N-VV22||--||PVC insulated PVC sheathed steel tape armored fire-resistant power cable|
|VV23||VLV23||PVC insulated PE sheathed steel tape armored power cable|
|VV32||VLV32||PVC insulated PVC sheathed thin steel wire armored power cable|
|Z-VV32||Z-VLV32||PVC insulated PVC sheathed thin steel wire armored flame-retardant power cable||Lay indoors, in mine shaft and under water, able to bear certain mechanical fore and great pulling force.|
|N-VV32||--||PVC insulated PVC sheathed thin steel wire armored fire-resistant power cable|
|VV33||VLV33||PVC insulated PE sheathed thin steel wire armored power cable|
|VV42||VLV42||PVC insulated PVC sheathed thick steel wire armored power cable|
|Z-VV42||Z-VLV42||PVC insulated PVC sheathed thick steel wire armored flame-retardant power cable|
|N- VV42||--||PVC insulated PVC sheathed thick steel wire armored fire-resistant power cable|